Another possibility is the following:. To change a parameter value operates as follows:. Enter the Programming mode. Select the required parameter. NOTE : the set value is stored even when the procedure is exited by waiting the time-out to expire. Keep pressed for more than 3 s the and keys.
|Country:||Trinidad & Tobago|
|Published (Last):||27 September 2016|
|PDF File Size:||7.35 Mb|
|ePub File Size:||11.86 Mb|
|Price:||Free* [*Free Regsitration Required]|
Quick Links. ICC Series. Table of Contents. Multifunction split controller for medium and low temperature ventilated applications with twin compressors 5 pages. Digital controller with off cycle defrost and aux relay 4 pages. Digital controller with defrost and fan management 5 pages.
Dead band digital controllers with multi probe input 4 pages. Digital controller with defrost and fans management 4 pages. In programming mode it selects a parameter and confirm its value. Depending on the programming, push it for 5 s to run the unit in Chiller or Heat Pump mode. During the programming it scrolls the parameter code or decreases its value. Symbol Function If pushed for 5s it allows to start the unit in Heat pump chiller or heat pump function.
If pushed for 5s it allow to start the unit in Chiller chiller or heat pump function. Push SET: the lower display shows Pas while the upper display 0 blinking. For wall mounting use the V-KIT plastic adapter as illustrated in figure 2. Maintenance icon lighted procedure Anti - freeze Water Supply Cond. Only with active input is possible to change the functioning again through o and n keys. The hour before turning to manual reset procedure counting stops if the compressor stops or if the AL03 Low alarm detection with unit in Off or Stand-by.
The after alarm event. Accuracy ambient temp. Print page 1 Print document 38 pages. Cancel Delete. Sign In OR. Don't have an account? Sign up! Restore password. Upload from disk. Upload from URL.
Dixell 121C Controller
dixell ichill IC100C series Instruction Manual